52041 Badia Al Pino
Arezzo - Italy
The demineralization process is needed in order eliminate water salinity. It is achieved by means of exchange resins, (“strong” Cationic and “strong” Anionic), which can be regenerated from hydrochloric acid and sodium hydroxide (4-8% HCl + 4-8% NaOH).
The resins are contained in 2 special cylinders with polyethylene inner shell.
The water is supplied by means of the pressure existing in the water network, alternatively the system can be equipped with an optional pump and storage and settling tanks.
The demineralisation capacity depends on the concentration of minerals in the starting water and on the presence of any other substances.
Each liter of resin has a nominal capacity to retain up to 25gr of CaCO3.
The system consists of:
The two columns containing the resins are used in series and to optimize the yield, it is possible to invert them when the conductivity of the water reaches the threshold of 20 μS/cm. the second column, less saturated, becomes the first to meet the water flow, until the conductivity meter signals that the second column is also saturated. At this moment the resins must be regenerated by countercurrent flow of a solution of hydrochloric acid and sodium hydroxide (4-8% HCl + 4-8% NaOH).
|Production Capacity||500 l/h @2-3 bar||1000 l/h @2-3 bar|
|Resin Colomn||No.2 x 33 l||No.2 x 63 l|
|Resin Quantity||2 x 25 l||2 x 50 l|
|Total Resin Capacity||1250 g CaCO3||2500 g CaCO3|
|Water Initial conductivity||< 2 μS/cm||< 2 μS/cm|
|Water Conductivity with saturated resins||20 μS/cm||20 μS/cm|
|Power Supply||15 W - 230V 1F 50/60Hz||15 W - 230V 1F 50/60Hz|
|Overall Dimensions (LxWxH)||800 x 400 x 1800 mm||800 x 400 x 1800 mm|